This is for more general topics about networking and vendors.
5 posts • Page 1 of 1
Hi I am trying to find an excel sheet which will show me exact requirements for RRAing certain TelePresence systems.Need one for a TelePresence 3000 series for now. Need a form which gives exact measurements etc, power requirements.I have a Cisco TelePresence Fundamentals book but can be difficult to find exact specifications.
Here it is... for more details request for ciscoet.com access Room Size Minimum Depth / Width / Height- 15’ x 20’ x 8’ 4.6m x 6m x 2.44m Lighting- 300-400 lux Facial Light (vertical plane) Twice the facial light or less for Shoulder Light (work surface) Acoustics- Ambient Noise 45dBA SPL NC30 Reverberation 150-700ms Acoustic Panel on Side walls Power- 4.56kW Max 4 dedicated circuits Participant convenient ports consume additional power Independent Room ControlHVAC- Typical Cooling 11,200 BTU/Hr DesignAesthetic Continuity highly desirableFor best video quality: - Avoid high contrast elements such as very dark or bright colors- Avoid glossy finishes- Avoid clutter